Q. When can I make a splice in a conduit body? A. Splices are permitted in conduit bodies that are legibly marked by the manufacturer with their volume and the maximum number of conductors permitted in a conduit body is limited in accordance with 314.16(B) [314.16(C)(2)]. However, capped elbows, handy ells, and service-entrance elbows aren’t permitted to contain any splices.
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.