Find the Answer
"It took us a while to find this panel," said Bob Lynch, owner of Robert Lynch Electrical Services in Center Harbor, N.H.
The most obvious violation here is with 110.26, Spaces About Electrical Equipment. There's no way this installation permits ready and safe operation and maintenance of equipment. A lack of working space 110.26(A), clear space 110.26(B), and dedicated equipment space 110.26(F) can all be cited in this instance.