How well do you know the Code? Think you can spot violations the original installer either ignored or couldn't identify? Here's your chance to moonlight as an electrical inspector and second-guess someone else's work from the safety of your living room or office. Joe Tedesco, who has a knack for finding shoddy electrical work, did the dirty work and found this mess. Now it's your turn to identify the violation.
I found this section of metal wireway in the attic of a tall building during an electrical inspection. The wireway was not only missing its covers, but at some point in time someone had used this area as a trash receptacle. This would no doubt add fuel load in this space if a fire were to break out in this area. In addition, the blocks used to support the conductors are not a recognized method of installation.