How well do you know the Code? Think you can spot violations the original installer either ignored or couldn't identify? Here's your chance to moonlight as an electrical inspector and second-guess someone else's work from the safety of your living room or office. Joe Tedesco, who has a knack for finding shoddy electrical work, did the dirty work and found this mess. Now it's your turn to identify the violation.
Find the Answer
The Fine Print Note (FPN) of 300.3(C)(1) refers us to Sec. 725.136(A) for Class 2 and Class 3 circuit conductors, which does not allow you to place Class 2 and Class 3 circuit conductors in the same raceway as Class 1, electric, light and power conductors.