Aug 23, 2012 | Electrical Construction and Maintenance
In this episode, Russ finds a corroded section of RMC and discusses the supplemental corrosion protection requirements of Section 300.6(A)(3).
- Moving Violations 1
- Stumped by the Code? NEC Requirements on Grounding Electrode Requirements for Separately Derived Systems and GFCI protection Requirements of Space-Heating Cables 3
- Updated Requirements for Services and Overcurrent Protection 1
- Stumped by the Code? Requirements for the Interrupting Protection Rating of Overcurrent Devices, NM Cable Installation Rules, and More
- UL Warns of EMT with Inadequate Corrosion Protection