Electrical Talk Pics & VideosCommented on: 1 year ago (March 27, 2014)
Two things are wrong. One is that a 20A circuit was used to power it up because it's a 15A GFCI and when the conductors were installed it wasn't torqued properly. This created arcing when it was...
The installer was too lazy to route it into a proper grounding means.
I agree with you
The picture is not very justifiable because it doesn't show whether it is a 480V tap or not, or even a type of panel.
The installer doesn't know the Electrical Codes. Any HVAC person doesn't know the Electrical Codes.
Well, since the electrician was color blind & obviously the other electrician knew about his problem he should had looked over his final connections just to make sure.