Electrical Talk Pics & VideosCommented on: 2 years ago (March 27, 2014)
Two things are wrong. One is that a 20A circuit was used to power it up because it's a 15A GFCI and when the conductors were installed it wasn't torqued properly. This created arcing when it was...
Should had a 1900 box for splicing the cable with the proper connectors.
The installer was too lazy to route it into a proper grounding means.
I agree with you
The picture is not very justifiable because it doesn't show whether it is a 480V tap or not, or even a type of panel.
The installer doesn't know the Electrical Codes. Any HVAC person doesn't know the Electrical Codes.