Electrical Talk Pics & VideosCommented on: 2 years ago (March 27, 2014)
Two things are wrong. One is that a 20A circuit was used to power it up because it's a 15A GFCI and when the conductors were installed it wasn't torqued properly. This created arcing when it was...
Who makes it and how much does it cost? (for cost effect)
I don't think it was an electrician that did this. It must have been someone that thinks he/she is an electrician. But that is a disaster waiting to happen, if it didn't happen already!!!
Should had a 1900 box for splicing the cable with the proper connectors.
The installer was too lazy to route it into a proper grounding means.
I agree with you