Here's an earlier article that Mike Holt wrote for us on the topic of properly sizing conductors and protective devices for A/C and refrigeration equipment.
I corrected the error in the main text.
Yes. A third restriction was added in the 2011 Edition of the NEC calling for the addition of a warning label to be applied to the enclosure that identifies the closet disconnecting means for any...
Unfortunately, many of our older print articles (such as this one) appear on our website without their original graphics. Although the graphics are not available to post here...
Click on the "caught on video" hyperlinked text in the news summary above
So you don't enter the building through this door? :)
I"M POSTING THIS ON BEHALF OF A USER THAT WISHES TO REMAIN ANONYMOUS
I'm starting to wonder if OSHA isn't making a mistake by not prioritizing the paragraphs, in order of importance, and...
No one replied to this question. If they had then it would have shown up in the same location that our comments are showing up now.
Yes, this is definitely an option.
That's an excellent point to make, Paul.