With respect to the requirement of panic hardware on personnel doors of electrical equipment rooms, this hardwareis now required to be____________ per the 2014 NEC. A. approved B. labeled C. listed D. of any type (there are no specific requirements) Answer: C As noted in 110.26(C)(3) of the 2014 NEC, "Where equipment rated 800A or more that contains overcurrent devices, switching devices, or control devices is installed and there is a personnel door(s) intended for ...
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.