When installing disconnecting means for outside feeders and branch circuits, if the disconnecting means installed in accordance with Sec. 225.32 of the 2014 NEC is not readily accessible, it shall be _________. A. wet location rated. B. operated by a mechanical linkage from a readily accessible point. C. permitted to be electrically operated by a readily accessible, remote-control device in a separate building or structure in a multi-building industrial installation under single ...
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.