Q. What are the requirements related to the use of a ground rod for the grounding electrode system, including sizing of the grounding electrode conductor? (Answer based on 2011 NEC.) A. Ground rod electrodes must not be less than 8 ft in length in contact with the earth [250.53(G)]. Rod-type electrodes must have a diameter of at least 5/8 in., unless listed [250.52(A)(5)(b)]. Rod, pipe, or plate electrodes must meet the following requirements [250.53(A)]: 1) If practicable, rod, ...
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.