Q. What are the Code rules for sizing overcurrent protection for conductors? A. Except as permitted by (A) through (G), conductors must be protected against overcurrent in accordance with their ampacity after ampacity correction and adjustment as specified in Sec. 310.15 [240.4]. (A) Power loss hazard. Conductor overload protection isn’t required, but short-circuit protection is required where the interruption of the circuit will create a hazard; such as in a material-handling ...
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.