All questions and answers are based on the 2011 NEC. Q. What is the Code rule for sizing feeder conductors, both ungrounded and neutral? Please show an example. A. Section 215.2(A)(1) requires that the minimum feeder conductor ampacity, before the application of ambient temperature correction [310.15(B)(2)(a)], conductor bundling adjustment [310.15(B)(3)(a)], or both, must be no less than 125% of the continuous load, plus 100% of the noncontinuous load, based on the terminal temperature ...
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.