In this episode, Russfinds a sloppy installation of cables and a junction box. The installer violated at least two sections of the 2011 NEC (314.23 and 300.11) by using tape to mount a junction box and zip ties to hold cables to conduit.
Moving Violations Video No. 47, by Russ LeBlanc, NEC Consultant: Improper Cables & Junction Boxes
Sponsored Introduction Continue on to (or wait seconds) ×