Q. Is an equipment grounding conductor always required in a PVC raceway between the electric utility meter and service disconnect? Find the Answer A. Typically, an equipment grounding conductor is required in PVC, and when that is the case, a separate equipment grounding conductor of the wire type must be installed within the conduit [300.2(B) and 352.60]. However, there is an exception that deals with service raceways. Exception No. 2: An equipment grounding conductor isn’t ...
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.