Q. How do I size the conductor and overcurrent protection for an air-conditioner? (Answer based on 2011 NEC.) Find the Answer A. The short circuit and ground fault protective device for a single motor compressor must not be more than 175% of the motor compressor current rating. If the protective device sized at 175% isn’t capable of carrying the starting current of the motor compressor, the next size larger protective device can be used, but in no case can it exceed 225% of the motor ...
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.