Switches controlling line-to-neutral lighting loads must have a neutral provided at the switch location unless _____. a)the conductors for switches enter the device box through a raceway that has sufficient cross-sectional area to accommodate a neutral conductor b)cable assemblies for switches enter the box through a framing cavity that’s open at the top or bottom on the same floor level, or through a wall, floor, or ceiling that’s unfinished on one side c)the ...
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.