Nonmetallic cables can enter the top of surface-mounted cabinets, cutout boxes, and meter socket enclosures through nonflexible raceways not less than 18 in. or more than _____ ft in length if all of the required conditions in Sec. 312.5(C) are met. a) 3 b) 10 c) 25 d) 100 See answer and applicable Code reference The correct answer is: b) 10 Article 312 of the 201 NEC covers cabinets, cutout boxes, and meter socket enclosures. An Exception in 312.5(C) states, "Cables with entirely ...
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.