Generally speaking, the NEC states that conductors for lighting or power may occupy the same enclosure or raceway with conductors of power-limited fire alarm circuits. a) True b) False See answer and applicable Code reference This statement is: b) False As noted in Section 760.136(A) of the 2011 NEC, "power-limited fire alarm circuit cables and conductors shall not be placed in any cable, cable tray, compartment, enclosure, manhole, outlet box, device box, raceway, or similar fitting ...
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.