Floor-mounted flat conductor cable and fittings shall be covered with carpet squares no larger than _____. a) 18 inches square b) 24 inches square c) 30 inches square d) 36 inches square See answer and applicable Code reference The correct answer is: d) 36 inches square Article 324 outlines the requirements for flat conductor cable (Type FCC). As noted in 324.41, "Floor-mounted Type FCC cable, cable connectors, and insulating ends shall be covered with carpet squares not larger ...
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.