For equipotential bonding of pool and spa equipment, a solid 8 AWG copper conductor shall be run back to the service equipment. This conductor shall be unbroken. a) True b) False See answer and applicable Code reference The correct answer is: b) False The installation requirements for permanently installed pools are outlined in Part II of Article 680 in the 2011 NEC. As noted in Sec. 680.26(B), "The parts specified in 680.26(B)(1) through (B)(7) shall be bonded together using solid ...
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.