The connection of the grounding electrode conductor to a buried grounding electrode (driven ground rod) shall be made with a listed terminal device that is accessible. a) True b) False See answer and applicable Code reference The correct answer is: b) False The requirements for grounding electrode conductor and bonding jumper connections to grounding electrodes are noted in Sec. 250.68 of the 2011 NEC. Exception No. 1 in 250.68(A) states, "An enclosed or buried connection to a ...
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.