Under seven conditions described in Sec. 240.21(A) through (H) of the 2014 NEC, you don’t have to install an overcurrent protection device (OCPD) at the point of conductor supply [240.21]. The condition occupying most of the space in this Section of the Code is where you have feeder taps. A close second for space is where you have transformer secondary conductors [Sec. 240.21(C)]. This condition has six variations by type of application: Protection by primary OCPD. Secondary ...
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.