Change No. 5: Section 210.71 (Meeting Rooms)
New rules require receptacle outlets for meeting rooms in commercial occupancies. 210.71 Meeting Rooms (A) General. Meeting rooms not larger than 1,000 sq ft must have receptacle outlets for 15A or 20A, 125V receptacles in accordance with 210.71(B). Where a room or space is provided with a movable partition(s), the room size must be determined with the partition in the position that results in the smallest size meeting room. Note 1: Meeting rooms are typically designed or intended for ...
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.