Change No. 3: Section 210.8 (GFCI Protection)
Appliance GFCI requirements were relocated to Sec. 422.5, measuring and GFCI requirements for receptacles near sinks were clarified, GFCI requirements for unfinished basement and non-dwelling receptacles were clarified, and new requirements were added for crawl spaces. Ground-fault circuit interruption for personnel must be provided as required in Sec. 210.8(A) through (E). The GFCI device must be installed at a readily accessible location. Note 2: See Sec. 422.5 for GFCI requirements ...
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.