Change No. 23: Section 695.15 (Surge Protection)
Fire pump controllers must now have surge protection. 695.15 Surge Protection. A listed surge protection device [Art. 285] must be installed in or on the fire pump controller. Analysis: Few people argue the advantages of having surge protection. In a commercial building, the computers probably all have surge protection, but the fire pump controller doesn’t. A study was conducted, commissioned by the NFPA Fire Protection Research Foundation, and it concluded that 12% of the fire ...
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.