Change No. 15: Section 440.9 (Grounding and Bonding)
A wire-type equipment grounding conductor is now required for some air-conditioning installations. 440.9 Grounding and Bonding. Where metal raceway is run exposed on a roof for air‑conditioning and refrigeration equipment, an equipment grounding conductor of the wire type must be installed within the outdoor portions of metal raceways using non-threaded fittings (Fig. 15). Analysis: Electrical metallic tubing (EMT) is permitted to be used as an equipment grounding conductor (EGC) ...
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.