Change No. 13: Section 404.22 (Electronic Lighting Switches)
A new rule requires electronic switch manufacturers to use a neutral for return current, not the equipment grounding conductor. 404.22 Electronic Lighting Switches Effective January 1, 2020, electronic lighting control switches must be listed to not introduce current on the equipment grounding conductor during normal operation (Fig. 13). Exception: Electronic lighting control switches that put current on the equipment grounding conductor [404.2(C) Ex] must be listed and marked for use ...
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.