Change No. 15: Grounding and Bonding Transformer Enclosures
Transformers are now required to have a place to terminate conductors. Article 450 Transformers and Transformer Vaults Part I. General Provisions 450.10 Grounding (A) Dry-Type Transformer Enclosures. Where separate equipment grounding conductors and supply-side bonding jumpers are installed, a terminal bar for these conductors must be installed inside the enclosure. The terminal bar must not cover any ventilation openings (Fig. 30). Exception: Where a dry-type transformer is equipped ...
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.