Change No. 14: Switch Connections
The requirement for having a neutral at switch locations was revised. Article 404 Switches I. Installation 404.2 Switch Connections (C) Switches Controlling Lighting Loads. Switches controlling line-to-neutral lighting loads must have a neutral provided at the switch location other than in the following locations: (1) Where the conductors for switches enter the device box through a raceway that has sufficient cross-sectional area to accommodate a neutral conductor. (2) Where the ...
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.