Change No. 9: Type of Disconnect
The rule requiring building disconnects to be “suitable for use as service equipment” has been extensively revised. Article 225 Outside Branch Circuits and Feeders Part II. Buildings or Other Structures Supplied by a Feeder(s) or Branch Circuit(s) 225.36 Type. The building/structure disconnecting means can be comprised of a circuit breaker, molded case switch, general-use switch, snap switch, or other approved means. If an existing building uses the neutral conductor for ...
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.