Overcurrent protection devices (OCPDs) need protection, too. Not from overcurrent, but from physical damage [240.30(A)]. You can provide that protection in one of two ways: 1. Put them in something: an enclosure, cabinet, cutout box, or equipment assembly. 2. Mount them on something: open-type switchboards, panelboards, or control boards. The second option is available only if what you’re mounting the OCPD on is: 1. In a room or free from dampness and ignitable material, and 2. ...
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.