The main drive motor for Line 3 has been replaced three times in as many years. The CFO knows your reputation as a crack troubleshooter, and she’s told the plant manager that unless he wants to keep buying replacement motors, to have you solve the failure cause. After the second failure, a power analyzer was installed on the feeder. It shows a (corrected) PF of 96% at the motor, but the history doesn’t show any power event that could have caused the latest failure. To live up to ...
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.