In Part 6, we started talking about Part III of Article 230 in the NEC. Specifically, we noted that it begins by requiring that the conductor be insulated for the applied voltage [230.30]. New with the 2014 NEC, 230.30 has a Part B. This is a list of wiring methods permitted for underground service conductors. If you look in the Chapter 3 Table of Contents, you will see an Article for each of these wiring methods. It’s nice to have a list right at this point. This is a usability ...
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.