Service entrance cables have special mounting requirements. You must support them within 12 in. of every service head, gooseneck, or connection to a raceway (or enclosure) [230.51(A)] in that run. The maximum interval between supports for a service entrance cable is 30 in. What exactly is a gooseneck? It’s a loop-down in the cable, put there to prevent water from running along the cable and entering the service entrance. The shape it takes on resembles the neck of a goose, thus the ...
Verified Website Registration Required to Access this Content
Only registered, verified users have access to Gold content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.
If you have already registered, please verify your account credentials to access this content.
(Email verification can be re-sent by going to youraccount