Stumped by the Code?
Q. We recently bid a project that involved a stackable washer/dryer in each dwelling unit of an apartment building supplied by a single 30A, 240V receptacle circuit. The inspector says we must install a 20A, 120V laundry receptacle circuit in addition to the 30A, 240V receptacle circuit. This makes no sense to me. A. The Code doesn't provide for an exemption to the rule in 210.11(C)(2) and 210.52(F)