Nonmetallic cables can enter the top of surface-mounted cabinets, cutout boxes, and meter socket enclosures through nonflexible raceways not less than 18 in. or more than _____ ft in length if all of the required conditions in Sec. 312.5(C) are met. a) 3 b) 10 c) 25 d) 100
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.