Illumination shall be provided for all working spaces about service equipment, switchboards, panelboards, and motor control centers _____. a) over 600V b) located indoors c) rated 1,200A or more d) using automatic means of control
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.