In one- and two-family dwellings, the grounding conductor for CATV shall be as short as practicable, not to exceed _____ in length. a) 5 ft b) 8 ft c) 10 ft d) 20 ft
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on EC&M allows you exclusive access to high value content centered around proprietary research, expert NEC analysis and in-depth technical procedures.