Hint: The line side into this switch was 500 kcmil for each phase. The load side conductors for each phase included seven No. 12 AWG Type THHN/THWN conductors.
Give the specific 1999 NEC references related to any violations you find. Write Joe a Violation Notice rather than sending in a copy of the Code rule. Send your response, in 25 words or more, to Joe Tedesco at 350 North St., Boston, MA 02113 or email@example.com. The winner(s) will receive $75. Please include your name, company name, job title, address, phone number and e-mail address. Previous winners are not eligible.